RMS-200 has general purpose I/O pins and Buttons for custom applications!
Below is a screen shot of the RMS-200 I/O overview page. Here you can choose which
of the boards Alarm or I/O pins to control. RMS-200 has 5 dedicated Alarm Pins that
have a corresponding LED. Use them with common door contacts to monitor entry points, or
use them for solar panel theft prevention. RMS-200 also has 4 general purpose pins
that can be set as Inputs or Outputs. These multi purpose I/O pins can be controlled or
read from either the web page interface or a command shell. RMS-200 also has 2 micro
push buttons that have special attributes when the RMS-200 board is booting. After
the RMS-200 board is finished booting these buttons are free for you to use for
controlling your devices.
Below is a screen shot of the RMS-200 I/O setup page for GPIO 1. GPIO pins can be
configured to be 3.3 volt Inputs or Outputs. Use these pins to control any manner of
devices, or sense condition changes and react with alerts or scripts.
Below is a pinout diagram of Con 8 on the RMS-200 board. These are 3.3 volt general
purpose I/O pins.
Pin 1 is VDD (3.3 volts).
Pin 2 is General Purpose I/O pin 1.
Pin 3 is General Purpose I/O pin 2.
Pin 4 is General Purpose I/O pin 3.
Pin 5 is General Purpose I/O pin 4.
Pin 6 is GND.
Below is a pinout diagram of the Alarm pins on the RMS-200 board. These input pins are pulled up to 3.3 volts.
JP1 - Pin 1 is Alarm input 1. Pin 2 is GND.
JP2 - Pin 1 is Alarm input 2. Pin 2 is GND.
JP3 - Pin 1 is Alarm input 3. Pin 2 is GND.
JP4 - Pin 1 is Alarm input 4. Pin 2 is GND.
JP5 - Pin 1 is Alarm input 5. Pin 2 is GND.
Below is a picture of the RMS-200 user programmable push buttons. Use these buttons to manually control devices, or use them for onsite testing of alerts or scripts.
Below is a screen shot of the RMS-200 Push Button 1 setup page. Add email alerts and run custom scripts or programs when a button is pushed.
Button 2 Note:
When the RMS-200 is booting up it first checks to see if Button 2 is being held down. If Button 2 is held down then all of the configuration files in /etc are re-written bringing the RMS-200 unit to a factory default condition.
Button General Note:
When the ALARM LEDS on the RMS-200 board perform a flashing sequence, the Linux OS has fully booted and normal button operation can commence.
EtherTek Circuits started its business in 2001. Ever since we have provided remote monitoring and control solutions for Remote Tower Sites, the Oil & Gas industry, Telemetry systems for Agriculture, Municipalities, Mines, Solar Farms, Hydro Plants, and the Military.
PO Box 1576,
Princeton, B.C. V0X-1W0 CANADA
+1 (250) 295-6794
+1 (250) 868-0448